Cooling system for poultry slaughtering
Project: Water chiller for vegetable on-line cooling
Purchaser: Shanghai Asia Pacific internationalvegetable co. LTD
The customer has 2t/h of salad vegetablecooling line, with two cooling tanks, and each tank can hold 3 tons of water.The temperature of the vegetables go into the water is designed to be 10degrees, after cooling the temperature is 3 degrees.
Need two ice water circulation chillers on eachcooling tank. The vegetables were circulated by 0~2 °C ice water, and thevegetables were cooled down to 3 °C.
Our design for customer:
There are 2 pre-cooling tanks in the productionline. Each pre-cooling tank is equipped with one set falling film chiller, and0~2° ice water flows directly into the water tank. Three units meet the heatexchange capacity of two pre-cooled water tanks.
The falling film chiller is placed next to thepre-cooling tank or above the water tank. The water pump and control cabinetcan be placed in the machine room, and the air-cooled unit can be placedoutdoors.
Total installed power of the unit is28.5kw
Falling film chiller overall dimension is 1650×550×1400mm
Refrigeration unit overall dimension 500×1500×1500mm